digplanet beta 1: Athena
Share digplanet:

Agriculture

Applied sciences

Arts

Belief

Chronology

Culture

Education

Environment

Geography

Health

History

Humanities

Language

Law

Life

Mathematics

Nature

People

Politics

Science

Society

Technology

A zigzag transformer is a special-purpose transformer with a zigzag or "interconnected star" winding connection, such that each output is the vector sum of two (2) phases offset by 120°.[1] Its applications are for the creation of a missing neutral connection from an ungrounded 3-phase system to permit the grounding of that neutral to an earth reference point and also harmonic mitigation, as it can suppress triplet (3rd, 9th, 15th, 21st, etc.) harmonic currents,[2] to supply 3-phase power as an autotransformer (serving as the primary and secondary with no isolated circuits),[3] and to supply non-standard, phase-shifted, 3-phase power.[1]

9-winding zigzag transformer
Zigzag transformer

Nine-winding, three-phase transformers typically have 3 primaries and 6 identical secondary windings, which can be used in zigzag winding connection as pictured.[1] As with the conventional delta or wye winding configuration three-phase transformer, a standard, stand-alone transformer containing only six windings on three cores can also be used in zigzag winding connection, such transformer sometimes being referred to as a zigzag bank.[1] In all cases, six or nine winding, the first coil on each zigzag winding core is connected contrariwise to the second coil on the next core. The second coils are then all tied together to form the neutral, and the phases are connected to the primary coils. Each phase, therefore, couples with each other phase, and the voltages cancel out. As such, there would be negligible current through the neutral point, which can be tied to ground.[4]

Each of the three "limbs" are split into two sections. The two halves of each limb have an equal number of turns and are wound in opposite directions. With the neutral grounded, during a phase-to-ground short fault, a third of the current returns to the fault current, and the remainder must go through two of the three phases when used to derive a grounding point from a delta source.[5]

If one or more phases fault to earth, the voltage applied to each phase of the transformer is no longer in balance; fluxes in the windings no longer oppose. (Using symmetrical components, this is Ia0 = Ib0 = Ic0.) Zero-sequence (earth fault) current exists between the transformer’s neutral to the faulting phase. The purpose of a zigzag transformer in this application is to provide a return path for earth faults on delta-connected systems. With negligible current in the neutral under normal conditions, providing the defective load will be automatically disconnected in a fault condition, an undersized transformer may be used only as short-time rating is required (i.e. the transformer can only carry full rated current for, say, 60 s). Impedance should not be too low for desired maximum fault current. Impedance can be added after the secondaries are summed to limit maximum fault currents (the 3Io path).[6]

A combination of Y (wye or star), delta, and zigzag windings may be used to achieve a vector phase shift. For example, an electrical network may have a transmission network of 110 kV/33 kV star/star transformers, with 33 kV/11 kV delta/star for the high voltage distribution network. If a transformation is required directly between the 110 kV/11 kV network an option is to use a 110 kV/11 kV star/delta transformer. The problem is that the 11 kV delta no longer has an earth reference point. Installing a zigzag transformer near the secondary side of the 110 kV/11 kV transformer provides the required earth reference point.[7]

## References

1. ^ a b c d Lawhead, Larry; Hamilton, Randy; Horak, John (May 2006). Three phase transformer winding configurations and differential relay compensation (PDF). 60th Annual Georgia Tech Protective Relay Conference. pp. 8–10. Retrieved 27 December 2015.
2. ^ Khera, P.P. (October 1990). "Application of zigzag transformers for reducing harmonics in the neutral conductor of low voltage distribution system" (PDF). IEEE Trans. on Industry Applications. doi:10.1109/IAS.1990.152320.
3. ^ Sankaran, C. (1 July 2000). "The Basics of Zigzag Transformers". EC&M Magazine. Retrieved 22 February 2012.
4. ^ Post Glover – Zigzag Grounding Transformers
5. ^ Das, J.C. (2002). Short-Circuit Load Flow and Harmonics. CRC Press. pp. 25–28.
6. ^ Blackburn, J. Lewis, Protective Relaying, Marcel Dekker, Inc., New York, 1998
7. ^ URJA Techniques (india) Pvt. Ltd.

Original courtesy of Wikipedia: http://en.wikipedia.org/wiki/Zigzag_transformer — Please support Wikipedia.
 11337 videos foundNext >
 17 zig zag connections Grounding TransformersIntroduction to grounding transformer terminology and basics. Conexion Zig Zag Transformadores - Zig Zag transformerConexion de transformadores. CALCULATION OF ZIG ZAG TRANSFORMER ZERO SEQUENCE IMPEDANCECALCULATION OF ZIG ZAG TRANSFORMER ZERO SEQUENCE IMPEDANCE. (Part 2) Triple Frequency Voltages and Currents in TransformersThis is the second part of the story about triple frequency currents in power transformers and how they are dealt with by delta, wye, and zig-zag connections. Zig Zag Transformer CompaniesA special purpose 3 phase transformer, the zig zag transformer is able to provide grounding for electrical systems that otherwise would have none. Find out ... Vector Diagraming Transformer ConnectionsDennis Merchant video on vector diagrams for transformer connections. This video goes with 3rd year transformer connections units of instruction in the ... Introduction to the Delta Wye Transformer Connection Part 6a: Voltage Phasor DiagramIn part 6a, we'll talk about the voltage phasor diagram of the DAC or Dy11 transformer connection. Subscribe now to find out when part 6b will come out! (Part 1) Triple frequency voltages and currents in Power TransformersThe magnetic circuit of an electric power transformer is a non linear device. This non linearity is the source of higher harmonics of current (or voltage) in the ... Custom Transformer Manufacturers, Industrial, Power, Machine Control, Drive IsolationCustom Industrial Transformer Manufacturers with Design and Quality Manufacturing Expertise for Over 25 Years. At Controlled Magnetics, we don't just build ...
 11337 videos foundNext >

We're sorry, but there's no news about "Zigzag transformer" right now.

 Limit to books that you can completely read online Include partial books (book previews) .gsc-branding { display:block; }

Oops, we seem to be having trouble contacting Twitter